Peachtree Buffet & Grill for Lease.
Located at 915 Holcomb Bridge Rd Suite B, Roswell, GA 30076.
Driveway wraps around the building with a drive-thru window.
High traffic, middle to high income, high-density location.
Seating for over 100.
Long term lease available with options to renew.
Rent numbers on a new lease are $10,000 a month base rent plus about $1500 a monthly property tax and landlord insurance.
Convert to Any QSR, Fast Food w/Drive-Thru or Full-Service, Bar, Casual, Fine Dining Restaurant, Asian, Indian, Mexican, Taqueria, Juice Bar, BBQ, Seafood, Steakhouse, Retail or Professional Use.
Plumbing is primarily PVC (with some copper) for domestic water lines and PVC for waste lines. The plumbing fixtures observed are in good condition and no problems were noted or reported. The existing 80 gals high recovery water heater is sufficient for the needs of the restaurant.
The proper number of toilet fixtures are all handicap accessible in accordance with Georgia Code and are all in good working order. Proper signage and accessories meeting ADA requirements have been installed.
Power is provided from a pad-mounted transformer at the side of the building with 277/480 main service underground to an 800 amp rated main disconnect switch located on the exterior wall on the rear of the building. The main breaker serves two distribution panels located inside the shed-roofed addition on the rear of the building. One panel is rated at 200 Amps and has been abandoned. The remaining panel serves the rooftop packaged air conditioning units, kitchen equipment, and the general lighting and convenience outlets throughout the restaurant. These panels are configured to have served two separate spaces at one time, but now only serve the restaurant occupying the entire building.
Copper wiring is used for all interior wiring. It is assumed that the main service lines are aluminum although this could not be verified. If there is any aluminum wiring used for the main service, it is important for that aluminum wiring to be fitted with compression fittings and that infrared heat scanning be performed periodically to detect any “hot spots” at these connections indicative of deterioration of the wiring or connections. Generally, most electrical equipment and services appeared to be in good condition with no problems noted or reported.
TO VIEW PHOTO GALLERY AND MAXIMIZE SIZE CLICK ON ANY PHOTO AND USE YOUR ARROW KEY TO ADVANCE.
Click here to sign up for our free email alerts
to get new listings, price changes, updates and news.
If you need more information about this or any of our other listings,
please click here to electronically fill out our CA/NDA.